TPS B + C complex power surge protector is designed for low-power system-level constitutes I (Class B) and grade II (C grade) specially designed surge protection. Products are small, a large surge discharge capacity, low voltage protection level, fast response. Lifted restrictions decoupling between the installation and the length of the connecting wires between grade I and II stage surge protection, especially for the lightning arrestor (CLASS I) and surge protectors (CLASS II) between the two levels can not be met 10m the case of wire installation distances, saving installation space, simplifying installation techniques to optimize the wire connections.
TPS B+C/10 4P,TPS B+C/10 3P TPS B+C/10 3P+N,TPS B+C/10 2P TPS B+C/10 1P+N
TPS B + C complex power surge protector is designed for low-power system-level constitutes B (Class B) and grade (C grade) specially designed surge protection. Products are small, a large surge discharge capacity, low voltage protection level, fast response. Lifted restrictions decoupling between the installation and the length of the connecting wires between grade B and C stage surge protection, especially for the lightning arrestor (CLASS B) and surge protectors (CLASS C) between the two levels can not be met 10m the case of wire installation distances, saving installation space, simplifying installation techniques to optimize the wire connections.
large energy absorption (50kA, 10/350μs), output residual voltage, fast response time
active energy control assurance Class I, Class II module coordination of energy
provide comprehensive protection, combined with Class I, II level surge protectors respective advantages
modular, standard 35mm rail mounting, easy installation and maintenance
module with the deterioration of the instructions, and additional remote signal alarm
Remote signalling contact Diagram
|Type||TPS B+C 10||TPS B+C 10|
| Surge arrester classification:
IEC/VDE/EN requirement category
|I+II/ B+C/ T1+T2||I+II/ B+C/ T1+T2|
|Max. continuous operating voltage||UC||255 V||255 V|
|Impulse current ( 10/350μs )||Iimp||50 kA||50 kA|
|Voltage protection level at 50KA ( 10/350μs )||UP||≤1.5 kV||≤1.5 kV|
|Voltage protection level at 20KA ( 10/350μs )||UP||≤1.2 kV||≤1.2 kV|
|Specific energy for class I testI||W/R||625KJ/Ω||625KJ/Ω|
|Follow current interrupting rating||Ifi||3 KArms||500 Arms|
|Short-circuit withstand capability||50 KA||50 KA|
|*Max. backup fuse||125 AgL/gG||125AgL/gG|
|TOV characteristic||UT||385V / 5S||1200V / 200mS|
|Remote signaling contact||Option||—|
|Operating temperature||T||– 40 + 80|
|Tightening torque of terminals||4.5 Nm|
|Degree of protection||IP 20|
|Mounting rail||35 mm DIN-rail|
|10-35 mm2||16-35 mm2|
|10-35 mm2||16-35 mm2|
|10-50 mm2||16-50 mm2|
Applicable LPZ0A partition interface with LPZ2 mine, and installed in the main distribution system. It implements a direct parallel installation of two power surge protectors without the use of decoupling inductor, saving installation space due to the complexity of wiring and installation as a result of decoupling inductors, especially for an inter-stage secondary protection unable to meet the mounting distance of 10 meters circumstances, such as various types of communication base stations (room) computer room, separate dispatch centers and other low-voltage distribution line end total of two levels (B + C) surge protection; suitable for single-phase, TN, TT, IT and many other formats. TPS B + C/10 3P + N and TPS B + C/10 1P + N, is to build a TT / TN power systems “3 +1” and “1 +1” circuit protection specifically designed.
Installed in the mine district in LPZ0A-LPZ2 power line interface total distribution cabinet, the internal integration of the first, two power surge protection, power phase line (L), neutral (N), respectively, access Surge protection corresponding terminals ensure a solid and reliable, the surge protector ground and ground to make a good electrical connection.
No special maintenance, surge protectors should be regularly checked the work, where conditions can utilize power surge protector Remote alarm signaling functions. If protection status indicator window is red or front-limiting device operation, maintenance or replacement of the module should be timely.
TPS B+C 4P Wiring Diagram
TPS B+C 3P Wiring Diagram
TPS B+C 2P Wiring Diagram
|*1||21005||TPS B+C/10 3P+N||Three-phase five-wireB+C protect 7 modulars 3+1protect mode Iimp50KAUp≤1.5KV|
|*2||21006||TPS B+C/10 4P||Three-phase five-wireB+C protect 8 modulars Iimp 50KA Up≤1.5KV|
|*3||21007||TPS B+C/10 3P||Three-phase four-wireB+C protect 6 modulars Iimp 50KA Up≤1.5KV|
|*4||21008||TPS B+C/10 2P||Single-phaseB+C protect 4 modulars Iimp 50KA Up≤1.5KV|
|*5||21009||TPS B+C/10 1P+N||Single-phase B+C protect 3 modulars 1+1 protect mode Iimp 50KA Up≤1.5KV|
5 Stars (0)
4 Stars (0)
3 Stars (0)
2 Stars (0)
1 Star (0)
|Shipping Company||Shipping Cost||Estimated Delivery Time|
|3 - 7 days|
|3 - 7 days|
|5 - 14 days|
|Post Air Mail||Free Shipping||15 - 45 days|
|Return Policy||If the product you receive is not as described or low quality, the seller promises that you may return it before order completion (when you click "Confirm Order Received" or exceed confirmation timeframe) and receive a full refund. The return shipping fee will be paid by you. Or, you can choose to keep the product and agree the refund amount directly with the seller.
N.B.: If the seller provides the "Longer Protection" service on this product, you may ask for refund up to 15 days after order completion.
|Seller Service||On-time DeliveryIf you do not receive your purchase within 60 days, you can ask for a full refund before order completion (when you click "Confirm Order Received" or exceed confirmation timeframe).|